The sprinkler package shall include sufficient quantity of 165 or 212-degree heads placed no more than 7'6" from any wall, with coverage of approximately 130 square feet, with Schedule 40 Black Pipe. The complete fire sprinkler package shall meet the latest edition of the NFPA. The sprinkler system shall be fabricated as to adapt to existing fire sprinkler system at no more than two riser locations. Fire sprinkler tie-ins shall be brought to the perimeter of the modular structure. Final connection to existing fire sprinkler lines is by others.
URINAL - WALL MOUNTED
The urinals shall be made of vitreous china and shall come complete with a flush valve. Final plumbing connection to waste and supply lines are by others.
Toilets shall have white china bowl and tank and include a molded high gloss, white enamel finish toilet seat. There shall be an installation kit with all necessary supplies and instructions for connection to existing rough plumbing. Final plumbing connection to waste and supply lines are by others.
Bathroom sinks shall be white china with and include hardware for installation via wall hanging or vanity. Each sink shall include a dual control chrome plated faucet with die cast zinc handles. The faucet pack installation materials and instructions shall be included. Final plumbing connection to waste and supply lines are by others.
POWER STREAM INSTANT WATER HEATER
There shall be included a Bosch PowerStream Model RP1 instant water heater. The unit is rated at 9.5kw @ 240 volts and shall draw up to 40 amps. This unit can heat up to an 84-degree temperature rise @ .75 gallons per minute.